In any continuous manufacturing process such as steel production, increased throughput is the path to higher profits through maximum utilization of fixed capital investments. In order to achieve increased throughput, more sophisticated control systems are being deployed. These systems enable ever-higher levels of automation but can present new challenges in terms of managing system reliability. Maintenance of profit margins depends on the line remaining in production with minimal unexpected downtime.
It is essential that control components, such as sensors, be selected in accordance with the rigorous demands of steel industry applications. Standard sensors intended for use in more benign manufacturing environments are often not suitable for the steel industry and may not deliver dependable service life.
When specifying sensors for steel production applications, some environmental conditions to consider include:
High temperatures exist in many areas of the steel-making process, such as the coke oven battery, blast furnace, electric arc furnace, oxygen converter, continuous casting line, and hot rolling line. Electronic components are stressed by elevated temperatures and can fail at much higher rates than they would at room temperature. Heat can affect sensors through conduction (direct transfer from the mounting), convection (circulating hot air), or radiation (line-of-sight infrared heating at a distance). The first strategy is to install sensors in ways that minimize exposure to these three thermal mechanisms. The second line of defense is to select sensors with extended temperature ratings. Many standard sensors can operate up to 185° F (85° C) but high temperature versions can operate to 212° F (100° C) or higher. Extreme temperature sensors can operate to 320° F (160° C) or even 356° F (180° C).
Don’t forget to consider the temperature rating of any quick-disconnect cables that will be used with the sensors. Many standard cable materials will melt or break down quickly at higher temperatures. Fiberglass-jacketed cables, for example, are rated to 752° F (400° C).
Shock and Vibration
Steel making involves large forces and heavy loads that generate substantial amounts of shock under normal and/or abnormal conditions. Vibration is also ever-present from motors, rollers, and moving materials. As with heat, look for sensors with enhanced specifications for shock and vibration. For sensors with fixed mountings, look for shock ratings of at least 30 G. For sensors mounted to equipment that is moving (for example, position sensors on hydraulic cylinders), consider sensors with shock ratings of 100 to 150 G. For vibration, the statement of specifications can vary. For example, it may be stated as a frequency and amplitude, such as 55 Hz @ 1 mm or as acceleration over a frequency range, such as 20 G from 10…2000 Hz.
Don’t forget that the quick-disconnect connector can sometimes be a vulnerability under severe shock. Combat broken connectors with so-called “pigtail” or “inline” connectors that have a flexible cable coming out of the sensor that goes to a quick-disconnect a few inches or feet away.
The best way to protect sensors from mechanical impact is to install them in protective mounting brackets (a.k.a. “bunker blocks”) or to provide heavy-duty covers over them. When direct contact with the sensor cannot be avoided, choose sensors specifically designed to handle impact.
Another strategy is to use remote sensor actuation to detect objects without making physical contact with the sensor itself.
Corrosion and Liquid Ingress
In areas with water spray and steam, such as the scale cracker on a hot strip line, corrosion and liquid ingress can lead to sensor failure. Look for stainless steel construction (aluminum can corrode) and enhanced ingress protection ratings such as IP68 or IP69K.
When All Else Fails…Rapid Replacement
If and when a sensor failure inevitably occurs, choose products and accessories that can minimize the downtime by speeding up the time required for replacement.
Strategies include quick-change sensor mounts, rapid-replacement sensor modules, and redundant sensor outputs.
In the case of redundant sensor outputs, if the primary output fails, the system can continue to operate from the secondary or even tertiary output.
You can learn more about sensing solutions for the Steel Industry in Balluff’s industry brochure.